support the project

diagram of connecting

setting the pressure

catalogue

how it work

design

service

specifications

installation

**Calculation of an expansion tank** is performed to determine its volume, the minimum diameter of the connecting pipeline, the initial pressure of the gas space, and the initial operating pressure in the heating system.

The method of calculating expansion tanks is complex and routine, but in general, the following relationships can be established between the volume of the tank and the parameters affecting it:

- The larger the capacity of the heating system, the larger the volume of the expansion tank.
- The higher the maximum water temperature in the heating system, the larger the tank volume.
- The higher the maximum permissible pressure in the heating system, the smaller the volume of the tank.
- The smaller the height from the installation point of the expansion tank to the upper point of the heating system, the smaller the volume of the tank.

Since expansion tanks in the heating system are necessary not only to compensate for the changing volume of water but also to replenish minor hot-water leaks, a certain amount of water, called the operating volume, is provided in the expansion tank. In the calculation algorithm given above, the operational volume of water is laid down in the amount of 3% of the capacity of the heating system.

**Selection of an expansion tank** should be performed taking into account its temperature characteristics and strength. The pressure and temperature at the point of connection of the tank should not exceed the maximum permissible values.

The volume of the expansion tank must be greater than or equal to the volume obtained as a result of the calculation. There are no negative consequences from overestimating the volume, beyond the calculated one.

If the installation of expansion tanks is planned indoors, it should be taken into account that tanks with a diameter of more than 750 mm and a height of more than 1.5 m may not pass through the door, and mechanization means will be needed to move them. In this case, it is better to prefer not one, but several membrane tanks of smaller capacity.

**WARNING!**

1. When using glycol mixtures as hot-water, it is recommended to choose an expansion tank with a volume that is 50% larger than the calculated one.

2. The first sign of an incorrectly calculated expansion tank or its incomplete adjustment is when the safety valve often trips.

question : comment : feedback

Online Equipment calculations

Circulation pump

Booster pump

Heat exchanger for Heating

Heat exchanger for DHW

Expansion tank

Expansion vessel

Control valve

3 way control valve

Electric actuator

Balancing valve

Self-acting temperature controller

Safety valve

Differential pressure controller

Pressure reduction controller

Pressure relief controller

Flow controller

Pressure reduction valve

Auto bypass valve

Heat meter

Compact heat meter

Water meter

Y-Strainer

Check valve

Shut-off valves

Buffer storage tank

Tank water heater

Solid fuel boiler

1 217 | visitors yesterday |

visitors per month | |

17 891 | from United States |

49 243 | from all countries |